1. ## Fpm

Hey everyone.

1) Is there a calculation to keep my FPM the same through the whole duct system.

If so can you help me out with it?

I seem to keep it the same most of the way with my duct calculator.

But at some point things start to change.

2)
Or is it okay for it to change as long as my FPM dont go less then what my FPM state for that individual run at my desired friction rate?

3) also i heard try and keep my FPM at what my grill will allow?? Not sure if thats correct

Sent from my LG-M257 using Tapatalk

2. Originally Posted by Cool_man
Hey everyone.

1) Is there a calculation to keep my FPM the same through the whole duct system.

If so can you help me out with it?

I seem to keep it the same most of the way with my duct calculator.

But at some point things start to change.

2)
Or is it okay for it to change as long as my FPM dont go less then what my FPM state for that individual run at my desired friction rate?

3) also i heard try and keep my FPM at what my grill will allow?? Not sure if thats correct

Sent from my LG-M257 using Tapatalk
FPM of the grille has no bearing on the FPM your duct work should have.

Just stay within the range your duculater list.

3. Originally Posted by beenthere
FPM of the grille has no bearing on the FPM your duct work should have.

Just stay within the range your duculater list.
Okay i wasn't sure if there was an extra equation i can use maybe to keep that fpm maintained constant.

Sent from my LG-M257 using Tapatalk

4. CFM/sq ft=FPM

EG: 580 CFM through a 14x8 duct, ((14x8=112sq in)/144=.77 sq ft), 580/.77=753FPM

Your duculator should show the same FPM though.

5. Originally Posted by beenthere
CFM/sq ft=FPM

EG: 580 CFM through a 14x8 duct, ((14x8=112sq in)/144=.77 sq ft), 580/.77=753FPM

Your duculator should show the same FPM though.
Okay were did you get 144?

Sent from my LG-M257 using Tapatalk

6. Sq inches to sq feet conversion.

7. FPM changes as the ducting changes.

I'm guessing what you are trying to do is figure CFM.

Originally Posted by Cool_man
Hey everyone.

1) Is there a calculation to keep my FPM the same through the whole duct system.

If so can you help me out with it?

I seem to keep it the same most of the way with my duct calculator.

But at some point things start to change.

2)
Or is it okay for it to change as long as my FPM dont go less then what my FPM state for that individual run at my desired friction rate?

3) also i heard try and keep my FPM at what my grill will allow?? Not sure if thats correct

Sent from my LG-M257 using Tapatalk

8. Professional Member*
Join Date
Feb 2010
Location
On the water but near the hood
Posts
1,748
Post Likes
Get yourself some ACCA books and you'll understand you're asking the wrong question.
Last edited by btuhack; 11-03-2018 at 09:42 PM.

9. Originally Posted by BBeerme
FPM changes as the ducting changes.

I'm guessing what you are trying to do is figure CFM.
I was trying to see if i can keep the same fpm as my duct system starts and ends in design.

Sent from my LG-M257 using Tapatalk

10. To what end? Or, said another way, why?

Originally Posted by Cool_man
I was trying to see if i can keep the same fpm as my duct system starts and ends in design.

Sent from my LG-M257 using Tapatalk

11. Originally Posted by Cool_man
Okay were did you get 144?

Sent from my LG-M257 using Tapatalk
As said earlier. 144 sq in to a sq ft.

Look at your duculator. You should be able to see the FPM your duct size is capable of, and determine if your staying close to what you want. But keep in mind that its better to have a lower FPM than a higher one the further a way from the air handler/furnace you are.

#### Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•

## Related Forums

The place where Electrical professionals meet.