1. Professional Member*
Join Date
May 2004
Location
Malden Mass
Posts
376
Post Likes

## head loss math through field loops

Hi
There is a home with a geothermal system with 3- 500 ft loops in the side yard. Pipe is 1.25" polpy pipe.
I wanted to make sure the circulator pumps are not too small.
Calculation for 1-1/4" pipe moving 20 gpm (both heat pumps with both stages on)
through approx. 1600'= 5.6' per 100'= 5.6' X 16= 89.6' just from the field

Seems kind of high. Is this correct?

2. Regular Guest
Join Date
Mar 2015
Posts
11
Post Likes
Not hard to figure but need a little more info. Are loops 500' totqal length, piped in parrallel? What is pipe size in loop? How far from house to loops, and what pumps are you using? What is tonnage of units? If loop field is piped end to end you are in trouble. 20 gpm generally covers about 6-7 tons total.

3. Professional Member*
Join Date
May 2004
Location
Malden Mass
Posts
376
Post Likes
Originally Posted by Earth Power AC
Not hard to figure but need a little more info. Are loops 500' totqal length, piped in parrallel? What is pipe size in loop? How far from house to loops, and what pumps are you using? What is tonnage of units? If loop field is piped end to end you are in trouble. 20 gpm generally covers about 6-7 tons total.

4. Regular Guest
Join Date
Mar 2015
Posts
11
Post Likes
Nice diagram. The shunt pipes between all three loops concerns me. Are these vertical loops or horizontal? (It does not affect calculations, just curious. 510' loop are usually vertical made loops). All said, I'd have to get back to the office to run the loop calculations through software. Do you have fittings at the units to measure pressure drop across the unit and calulate flow? If those shunt pipes are in as shown the whole thing could be bypassing the loops.

5. Professional Member*
Join Date
May 2004
Location
Malden Mass
Posts
376
Post Likes
The loops are vertical. I was not there for the outside installation work, but The installer of the vertical loops, a major drilling company, is reputable company.
There are fittings, pete's plug to measure pressure drop.
My math is incorrect at the top of the post. I found out later the ground loop was installed in parallel
Because loops are in parallel, I found out the pressure drop is in the range of 40 to 50 feet through the ground loop in the field.

6. Regular Guest
Join Date
Mar 2015
Posts
11
Post Likes
Your head pressure is probably less than that. Probably closer to 25-30. Are you sure the loops are 1 1/4". Usually the main pipe will be that size and the loops 1" or 3/4". I'll run the numbers Monday for the fun of it. You should be able to get the charts on the units from Hydron, and measure pressure drop across the units to determine actual flow. Typically 3-5 psi pressure drops is normal.

7. Professional Member*
Join Date
May 2004
Location
Malden Mass
Posts
376
Post Likes
Originally Posted by Earth Power AC
Your head pressure is probably less than that. Probably closer to 25-30. Are you sure the loops are 1 1/4". Usually the main pipe will be that size and the loops 1" or 3/4". I'll run the numbers Monday for the fun of it. You should be able to get the charts on the units from Hydron, and measure pressure drop across the units to determine actual flow. Typically 3-5 psi pressure drops is normal.
The designer told me that the circuit was 1- 1/4". Don't know how the circuit was actually set up outside.
Correct the hydron unit is about that 4 to 6.5 depending on the stage. I thought the chart in the hydron manual was in feet of head but it might be psi. I am getting about 10 psi of static pressure near the supply manifold with pumps off.
I have about 7 psi at the inlet supply of one of the heat pump with system on and about zero psi on the return circuit that going down to the basement.

8. Professional Member*
Join Date
May 2004
Location
Malden Mass
Posts
376
Post Likes
Earth Ace,
I think my biggest issue is being able to read and know the correct pressure drop through out the system.
I do a lot of radiant heat and boiler systems. Basically this Geo system is a hydronic system that doesn't expand and contract
as say a boiler in the basement with baseboard circuits on the upper floors.
Seems like I need to get pressure readings then figure out if those readings are normal for this particular hydronic system.

9. Regular Guest
Join Date
Mar 2015
Posts
11
Post Likes
I ran the pipe sizing through my software and got a curve on your system. It looks like about 27' of head at 22 gpm. I had to guess at the flow resistance through the units but used a comparable unit so it should be close.

10. Professional Member*
Join Date
May 2004
Location
Malden Mass
Posts
376
Post Likes
Originally Posted by Earth Power AC
I ran the pipe sizing through my software and got a curve on your system. It looks like about 27' of head at 22 gpm. I had to guess at the flow resistance through the units but used a comparable unit so it should be close.
So that being said, the two Wilo pump model # 1.25 X 3.30 seem to be able to handle the head and the GPM for this system.
The pumps are set up in a push/pull arrangement.

11. Regular Guest
Join Date
Mar 2015
Posts
11
Post Likes
I did not look up the pump curves but calculated it with 2 Grundfos 1/6 HP pumps and they were just right.

12. Professional Member*
Join Date
May 2004
Location
Malden Mass
Posts
376
Post Likes
I am probably getting 27' at 22 gpm through the ground loop.
There are two flow meters in the supply pipes that go to each heat pump. The highest reading when both heat pumps are working is 8.5 gpm
each. I believe that the head must be higher than 27' because I am getting a total of 17 gpm and not 22 gpm of flow through the interior piping anyway. It seems like I need more head through heat pump supply circuit to overcome the friction losses in that portion of the system.

13. Regular Guest
Join Date
Mar 2015
Posts
11
Post Likes
That is a little low for correct operation. I will try to look up the pump curves on these pumps. I'm pretty sure my calculations are close.

#### Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•