When I first came to the house the T-stat was blank went to the airhandler the breaker was triped ,so I reset the breaker. After that turned the system to heat but only the airhandler came on. Then switched system to cool and whole system came on. When the system was on in cool 168LP 200HP ODT60 IDT73. Im new at this, If anyone can help.