Home is in SW Florida when I'm away for the summer. I wired my humidistat in series with my thermostat, when the temperture set point is met my fan comes on even though the humidistat set point is not. Here is how it's wired,
The outside unit is a heat pump, thermostat Aprilaire #8465
24v wired to RC/R and C
G wired to fan
Y to one side of humidistat the other side to the compressor (series)
W to aux. heat
o/b to reversing valve
My thinking is moving the G (fan) wire to the Y terminal would only let the fan come on with the compressor when both thermostat and humidistat set points are met instead of only the thermostat's set point. Will this work or is there a better way? Thanks for any help.