Wondering what the code says for sloping your pipe? I heard .5 " per 10 feet and 1 " per 10 feet , need a definite answer, much appreciated.
I would think it depends on how far away the object is that your trying to hit. Urinals are the easiest.
umm, what's in the pipe?
sorry i didn't specify which pipe, i meant in general for refrigeration piping, soon gonna be writing my exam, and just tryin gto cover all my grounds.
there is no code for sloping refrigeration piping(according to the international mechanical code). It is installed per manufacture's instructions which are different from company to company.
Hey dououie listen to Gino.
On Trane RAUC split systems 20-120 tons.
*Slope suction lines toward the evaporator 1/4 to 1" for every 10 feet.
*Slope liquid lines away from the condensing unit 1" for every 10 feet.
Thanks for the info , much appreciated..
Then give us the chapt and section and we can grade you.
Good luck on the test