New home, with an Amana unit in the upstairs. The AC installer came to me and said he would like to see separate runs of electrical to the unit, 60amp and 30amp breakers for the 15KW heat strip. AC installer says normal runs are 6 gauge to the 60 and a 10 gauge to the 30, from the main breaker panel.
The electrician has run a 4 gauge to a terminal box(lack of true name for the box)3ft from the unit. From here, he has a 6gauge to the 60 and a 10guage to the 30.
Since I am not a professional AC or electrical installer, I have to turn to you guys for your opinion.
Note: The AC company is a rather large company, serving several counties and has been here since 78. The installer has been with the company for 8years.
Electrical company is also a large company. The workers did not speak english very well,(not uncommon for Texas) so I wanted to get you guys professional opinion before I protest or not....