Adding a 3rd air return -- Bad Advice?
I have a 3 ton split heat pump for the upstairs of my home. At on end of the upstairs, I have a 20x16 air return. At the other end, I have a 35x13 room that has a 24x14 return. I'm getting ready to raise 2 walls in the 35x13 room to effectively make 2 rooms. One of the walls falls right in the center of the existing return, it has to be moved. I was thinking the best thing to do would be to move the return over and keep it in one room and then add another return to the 2nd room, that way both rooms have a return.
I called a local HVAC contractor to get a price to move one register and then add another return register in the other room. He said they would add another 24x14 register to the 2nd room (that way I wouldn't have to buy a different sized filters).
1) Will adding another 24x14 return mess my system up (too much air return)?
2) would the proper thing to do is remove the 24x14 and add 2 smaller registers?
You will not have a problem with to much air, the suggestion to use the same filter grill size is a smart idea.
Originally Posted by MrGrumpy48
no such thing as too much R/A
Adding more return will never hurt your system.
There is no bad beer, some just taste better than others.
Thanks for the responses. Sounds like the HVAC contractor knew what he was talking about.
Tags for this Thread