Can the Trane YCD102 rooftop unit be configured to only operate on low heat or 1st stage. Has anyone had success doing this ??
Why would you want to do this?
The unit is not old enough to replace with a lower heat unit, (which is all the customer needs per their heating requirements). And it will reduce their operating costs for gas.
yes and yes, but not for those reasons.
This can only go so far here in the open sections of the site. I would like to suggest getting your post count up, apply for Pro and get the details on the other side of the fence
Controls Forum Rules Site Rules Tridium
Deleted your duplicate thread on this. please don't make duplicate threads, thank you.
Contractor locator map
How many times must one fix something before it is fixed?
If the unit is controlled by Trane Tracer, I know you can disable the 2nd stage heat on the front end.
Thanks Hands !!
If it's a 2 stage unit, can't you just disconnect Y2? That way it should never call for the second stage.