With those numbers it does look like ckt 1 is overcharged. Subcooling at 32 and SH at 10 with 266psi head. What is your water entering temp? Are you sure the free cooling coil valve isn't leaking? For the low airflow, i would take Delta P across both coils together. What is your Delta T on this unit?