Hi, any help would be great..
ok so I was at this house earlier with a Ruud Hi efficient. start up furnace.. cb blower runs for 30 seconds then shuts off.. The condensate line coming off the bottom of the termination, was kinked badly in 2 spots. The furnace was running like this for 2 winters now.
After rolling the hose to get the kinks out, I got the furnace to fire up 3 times but not consecutively. I had condensate coming out the drain line to the sewer. Combustion Blower was making a slight slight gargle. barely noticeble. I was stumpt. cb blower is a bugger to remove..
Sorry no pics or model number. This is an upflow, Ruud Hi Efficient from 2003. The Hi and Lo pressure switches are both housed in a metal case. I've installed newer Hi efficients and noticed the new switches are housed in plastic.
Anybody else have trouble with these pressure switches before?? Im currently unemployed.. furnace is under warranty from the company i was previously with. they gave a good friend of mine a good deal so im sure they dont want to waste time servicing it.