Got a YCAJ chiller stating "no cool load"
I know this generally means that there is no load for the chiller to start, but this time round there is loads of load for the chiller to start.
Set-point is set for 6 oC and current LWT is 20 oC and still chiller states "no cool Load"
Checked the LWT sensor and it is reading correctly, decided to change the sensor anyway but still no joy.
I don't have experience with that chiller, but...
Is that setpoint the "active setpoint"?
Perhaps the active setpoint is referenced from a building controls source, and it is not what the local, or chiller panel, setpoint is.
Or the chiller panel could have its own reset enabled, and the resulting setpoint is higher.
So, an important question is, Is the chiller connected to any form of building controls?
Apologies, I should have said in my post.
No, the chiller is not connected to any building controls.
The only exception is, that the alarm contacts are wired to the building BMS.
So the chiller is completely dependent on Local mode only.
Need more info, but I'd suggest pulling up all the parameters and double checking them as a start,
Keep it simple to keep it cool!
Doubtful it would the Eproom as the chiller as all other parameters intact.
But it might be worth a shot if all else fails.
These are just guesses with the info you gave, what is the differential setting? (if it is wide could still be in range).
Is this controlling supply or return water temperature? Hopefully it has already been corrected and running fine.