Results 1 to 2 of 2
Thread: LENNOX GCS16-090
01-14-2006, 10:21 AM #1Professional Member
- Join Date
- Mar 2005
- CHATTANOOGA, TN.
Has anyone had the problem of blower control circuit locking in with no apparent fault ? Will only unlatch after disconnect is opened and reclosed. Unit may run for weeks before this happens again.
01-14-2006, 02:54 PM #2
my guess would be the k-25 time delay relay after looking at diagram. never had it happen so just a guess. would have to get in there with a meter and check it out before resetting.