# Thread: run time of current system

#### Hybrid View

1. Regular Guest
Join Date
Sep 2011
Posts
27
Post Likes

## run time of current system

Manual J says I need a 2.5 ton. I currently have 4 ton. Is there a way to time the cycle of my current system with a set point and outside temp to tell if I am currently over sized?

2. Professional Member*
Join Date
Jul 2006
Location
Virginia
Posts
6,772
Post Likes
on the hottest day of the year did your unit cycle on and off several times

3. There's a way to ball park it. Assume that your unit is maintaining an indoor/outdoor temperature difference of 10°. You clock the run times and find that the unit is running about 20 minutes out of the hour, or 33.33% of the time. Assuming that the heat load is proportional to the indoor/outdoor temperture difference, the unit would theoretically be able to maintain an indoor/outdoor difference of

10/(33.33/100) = 30°

if it were to run nonstop.

In reality the capacity of the system drops off as the ambient temperature increases, however the load isn't strictly propotional to the temperature difference either. The heat load does not increase at as great a rate as the temperature difference, so these two factors tend to cancel each other out to some extent.

This will be nowhere near exact, but if you find that your system is grossly oversized using this method, then it probably is grossly oversized in reality.

4. Professional Member*
Join Date
Feb 2010
Location
Cal
Posts
1,596
Post Likes
You are late to the party blue, follow the link.
Good luck.

5. Originally Posted by btuhack
You are late to the party blue, follow the link.
Good luck.

I remember that thread. A lot of good points raised. It would probably be more accurate to clock the runtimes on the hottest days. The percent runtime method would, for some not so obvious reasons, be more accurate at higher indoor/outdoor temp differences. I probably wouldn't try it with a temp difference below 15°.

6. Originally Posted by electricblue
Manual J says I need a 2.5 ton. I currently have 4 ton. Is there a way to time the cycle of my current system with a set point and outside temp to tell if I am currently over sized?

Is it more likely that a manual J is incorrect, or a rule of thumb used to size your current system?

7. Professional Member*
Join Date
Jun 2011
Location
Wake Forest, NC
Posts
353
Post Likes
Originally Posted by timebuilder

Is it more likely that a manual J is incorrect, or a rule of thumb used to size your current system?
We are assuming that the Manual J was done correctly. I have seen some really screwed up design parameters that have produced totally whacky load calculations.

So long as the calculation was done correctly, then go with that. If you aren't sure about the load calc, call another company and ask them to do one for you so you can compare results. Be prepared to pay for their time if you want to see the load calculation report.

#### Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•

## Related Forums

The place where Electrical professionals meet.