Results 40 to 40 of 40
Thread: Centravac failure
11-16-2011, 11:34 PM #40...One thought I did have was the CVHF 1300 has 2 actuator motors for the vanes , 1 for 1st stage and a separate 2nd stage actuator . The actuators must be set correctly to make sure the vanes are not being overdriven in the closed or open position . This would strain the vanes internally . Those hydraulic actuators have huge amounts of torque and could easily damage the vane assemblys if not set correctly .
Suggestions anyone ??The weak aren't destroyed by the strong.
The weak are destroyed by the under-estimated.
I know a famous song that ends in 'my nose'. The artist is dead. Know who?