View Poll Results: Do multiple Heat Pumps installed too close together work properly?
- 14. You may not vote on this poll
Results 14 to 20 of 20
Thread: Heat Pump Mystery
10-12-2011, 05:55 PM #14
yes your units are to close and it does have an affect on the. I also agree with you second contractor that moving the unit apart isnt going to resolve you real problem
at best it will help the units effiency but you from what you have said have other concerns going on there
make sure the systems are sized correctly and the ductwork is also sized properly this can also cause the units to not operate properly and run you bill up
before moving them and the expense of it find out the real problem fix it and then move the units
10-12-2011, 06:52 PM #15
Before choir, I walked around the side and saw the problem. Nine CU's, all enclosed by a privacy fence. Several feet of clearance, but it created a heat island with the fence on one side, and the building enclosing the other three sides.
The fence is gone this year. Bingo, all's well.
10-12-2011, 07:44 PM #16New Guest
- Join Date
- Oct 2011
I found a copy of the engineering data for my model and it states that there must be 24" between multiple units. I'm getting a lot of mixed input. On my poll, 9 have selected "Yes, multiple units installed too close together does effect their efficiency" and only one selected "no". Hoping to get the contractor who installed them to move one of the units about 4 feet to the left (have to accommodate my crawlspace door). Thanks for your input.
10-12-2011, 07:53 PM #17New Guest
- Join Date
- Oct 2011
I'm dealing with - but I don't have fencing around the units or any major obstructions apart from the units being only 8" apart. Not sure if that alone is enough to effect their performance. I spoke to yet another HVAC contractor today and he suggested getting both units running and feel the air expelled from the top of each one. Then, take a sheet of cardboard and insert it between the units while running and see if I can tell a difference in the temperature of the expelled air.
10-12-2011, 08:24 PM #18
High delta T will mean a good coil cleaning is in order.
BUT, I feel you root issues are elsewhere, as already mentioned here by others.
10-13-2011, 12:06 AM #19
1st, I did not read all the replies, so if this was said ignore it.
I think your question and the answers are a bit backwards/misleading.
"Do multiple Heat Pumps installed too close together work properly?
Yes - does effect performance and efficiency
No - doesn't effect performance or efficiency"
I think the "YES" and "NO" should be reversed, correct?If Guns Kill People, Do Pencils Misspell Words?
10-13-2011, 06:34 AM #20
I think you've struck on a valid issue but I also think you're spinning your wheels on a red herring. You need to have a highly qualified tech actually come out to your home and evaluate the system. This tech must know about the effects of airflow on system capacity and he must know how to properly charge a system using superheat and/or subcooling. He must be able to spot a dirty condensing unit as well as a dirty indoor coil, dirty blower wheel and closed or obstructed dampers. If he/she is lacking any of these skills, you're wasting your money to have him visit your home. I hate to admit it but you stand about a 1 in 50 chance at best of finding that individual in your area. I wish you success.