I am sizing hvac equip for a 1 story restaurant sports bar
the owners anticipate 200 people sometimes
The latent load is high due to max occupants and ventilation.
i want to keep things in percpective.
The kitchen is located in a separate room with exhaust and mua for hood
MUA is approx 70% exhaust
There are some existing package gas heat elec cooling units on roof
I have enough room on roof for a 10 ton roof unit. i was thinking of using two 5 ton splits instead.
My load calc is about 1 ton/ 125 sf +/-
If i try to satisfy all latent laod overall load is about 1 ton / 95 sf.
that seems rediculous