Newbies .... Walk up to OD unit and after checking current across the contactor terminals comming in you get 160 155 110 162 125 fluxuating all around on meter, checking line 1 to ground you get 120, line 2 to ground you get 40 volts.
Whats going on here ????
One for the Pro's .... walk up to a different unit , different neighborhood, and get 120 line 1 , 0 line 2 , go to main panel and get 120 , and 0 when checking to ground and neutral at MAIN breaker.
What tha hell ....