Results 14 to 18 of 18
Thread: service man's nightmare(I think)
01-04-2006, 07:17 PM #14
i charge flat rate also and on the few time with and problem that cant be found go back one time fee till it is found. then they pay for the repair. to just change parts till you find it isnt fair to the coustomer nor does it allow for learning.
you said he changed parts and then you think the gas valve was bad. but when you say it is still working means you arent sure it was the problem. probably was from what you have said but now the coustomer has paid for three calls and one control and one gas valve. how can this be fair to the coustomer? how is this fair to you also since you are the one being trained
changing parts till the problem doesnt happen any more is not service.
taking the time to find the problem and fixing it once is service. even if the repair has to wait till you can locate what is causing the problem
honesty,quality,and fairness is what we should strive for
01-04-2006, 08:37 PM #15Professional Member
Originally posted by Toolpusher
- Join Date
- Feb 2004
Originally posted by mike3
Cust should not not have to pay for us to learn
[Edited by mike3 on 01-04-2006 at 01:21 PM]
It's a matter of having the unit act up while your on the job [/B]
01-04-2006, 09:56 PM #16Professional Member
Originally posted by cmorris
- Join Date
- Oct 2001
- Waterford Michigan
Changed the valve and now the system is working fine. My question is I know that problems have to happens when we're there but what do you do when there is a problem but not when your there?
01-04-2006, 10:08 PM #17
When faced with multiple service calls on the same complaint or within a short period of time, you'd do well to bite the bullet and run through a thorough systematic checklist. Go through everything from gas piping, valves, sizing, meter capacity, inlet pressure studies under load, etc. then full electrical from power coming in through the system, then controls including every switch, contact, & gizmo and burner orifice spuds, primary and secondary air, pressures, cleanliness, firing, and then venting all the way out. Don't forget makeup air and house pressure diagnostics. This may seem like a lot but it cuts to the chase, leaves no stone unturned, and minimizes customer frustration. If it works, you turn lemons into lemonade.
02-13-2006, 09:05 PM #18Professional Member
- Join Date
- Jan 2003
If you have a problem like that you keep cycling the furnace until it shows up. When the controller locks out it points to where the problem is..(flash, flash, flash)\