Goodman Furnace Problem
I am fixing one goodman furnace(Model GMV90703BXA). when calling heat, the induced draft blower starts up. But just runs few seconds, then stops. The LED on the control board continues flash. I already check out the polarity of 115v power and wires. every thing is fine. Anybody can help me what the next is? Thanks.
Sorry, we cannot offer DIY advice on this site.
Originally Posted by george xue
If you're a professional, you can get your post count up to 15 and apply for Professional Membership.
If you're not a professional, you're probably best off calling a professional. We've built a locator map that you can find in my signature line.
George, if you are working as a pro in the HVAC business, get your post count up and apply for pro membership. Then, we can help you in the Pro residential forum.
'Till then, JP is correct. We can't offer DIY instruction.
[Avatar photo from a Florida training accident. Everyone walked away.]
2 Tim 3:16-17
RSES CMS, HVAC Electrical Specialist
AOP Forum Rules: