1. Regular Guest
Join Date
Dec 2004
Posts
24
Post Likes
for my own curiousity i clocked my gas meter, what would be my ratings in btu's .01 cubic meter dial 19 seconds per revolution the .05 cubic meter dial 111 seconds. the charts i checked show conversion for cubic feet only. thanks.

2. blk
Professional Member
Join Date
Jan 2005
Posts
475
Post Likes
aprox.67000btuh

3. Regular Guest
Join Date
Dec 2000
Posts
1,227
Post Likes
Btu per cu.ft. varies by region and their source of natural gas. In my area, about 1025 Btu/cu.ft.

4. I know I'll probably hear about using the dreaded Rule of Thumb but 1000 btu's/cu. ft. will get you pretty close for an initial observation.

5. Professional Member
Join Date
Nov 2003
Posts
51
Post Likes
another rule of thumb is every full revolution of the 1/2 ft dial on the gas mtr is 30,000 btu's. you clock the mtr for 1 minute 4 revs=120,000 btu's

6. Regular Guest
Join Date
Dec 2004
Posts
24
Post Likes
my meter shows in cubic meters not cubic ft, on the charts i have seen the conversions are for cubic ft. this is where i'm stuck on finding the btu input.

7. blk
Professional Member
Join Date
Jan 2005
Posts
475
Post Likes
I have a chart for clocking metric meters and as stated earlier on a .01 m3/rev test dial @ 19 sec/per rev you are looking at approx. 67 cubic feet /hour or 67000btuh ( based on 1000btuh/cubic foot)You can use the same formula for calculating input as you would on a standard meter using 3600 divided by the time for 1 revolution of your test dial and mutiplying by either .01 or.05 which will give you M3/HR. then multipy this by 10.35kWh/m3 which will give you the input in kilo-watts. Then knowing 1kw=3412btuh you can figure out the input.HTH

8. Regular Guest
Join Date
Nov 2005
Location
Kansas City (zip 66204)
Posts
50
Post Likes

## Will this help?

1 cubic meter is ~35.3147 cubic feet.
1 cubic foot is ~.02831685 cubic meeters.

I don't know if that will help you or not, but I though that you mighr be able to convert you reading into cubic feet with that.

Doug

9. Regular Guest
Join Date
Dec 2004
Posts
24
Post Likes
Thanks to blk and dougjrs, thats the formula i was looking for.

10. Professional Member
Join Date
Jan 2005
Posts
149
Post Likes
Here is a link to a handy gas clocking calculator
http://http://www.cozyparts.com/calc...gas_input.aspx

#### Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•

## Related Forums

The place where Electrical professionals meet.