ive been everywhere can someone supply me with one
i don't know why i use this stuff...
401 at the end
A and B
Find a Contractor by clicking here
So you can post in the AOP areas, Click here to get your * by your Pro Membership title.
Main Site Rules
How to become a Pro Member
NEW HTALK MEMBERSHIP MAP Click on additions/add marker
Here's another one.
I use it because it's the only one that works well for old R12 LT systems.
The Educational Forums
AOP Contractor Locator Map
thanks guys..but somethings...weird..
i have a tp chart put out by tecumseh...
and it dosnt match what the honeywell chart says..
techumseh mp39 @ 0*f =6.7 psi
honeywell mp39 @ 0*f =8.0 psi
hmmm? 22 was the same and 409 was real close..K-pasa?
am i spliting hairs?
the honeywell chart is the same as the one I gave you...
DuPont's P/T chart shows 7.4 psig at 0ºF for R401A (MP39): http://refrigerants.dupont.com/Suva/...pdf/k10909.pdf