Results 1 to 10 of 10
Thread: How Is A-Coil Supported?
09-16-2011, 10:55 AM #1Professional Member*
- Join Date
- Aug 2007
How Is A-Coil Supported?
I have a traditional system where the A/C A-coil resides above a vertical upflow gas furnace.
How is the weight of the A-coil supported? From below, by the furnace, or from above, by the supply duct?
I'm getting the furnace replaced and the new furnace will be significantly shorter than the existing one. I'm also wondering what is the best install method to adjust for this height difference.
09-16-2011, 11:54 AM #2
a no-brainer for a good install crew. They should be able to answer all your questions.GO NAVY, BEAT ARMY!
A DECADE OF DOMINANCE! +1
09-16-2011, 12:52 PM #3Professional Member*
- Join Date
- May 2008
As Greg said, a good experienced install crew can easily take care of this. Make sure you get one!!
09-16-2011, 02:31 PM #4
Support is just one of the considerations to coil installations. Air contamination from system drains. Type of furnace heat exchanger and Manufactures recommendations for height above it, Air flow and restrictions, air speed and volumes, appropriate temperature rise for heating system after a coil's install, correct temperature fall across the coil....... Yikes better call a qualified guy. With years of installation experience as a tin knocker I get my cousin involved with AC installs, he is a refrigeration mechanic and with him there I know I wont have to come back and listen to performance complaints.
09-16-2011, 04:17 PM #5The picture in my avatar is of the Houston Ship Channel and was taken from my backyard. I like to sit outside and slap mosquitos while watching countless supertankers, barges and cargo ships of every shape and size carry all sorts of deadly toxins to and fro. It's really beautiful at times.....just don't eat the three eyed fish....
¯`·.¸¸ .·´¯`· .¸>÷÷(((°>
`·.¸¸..· ´¯`·.¸ ¸.·´¯` ·.¸>÷÷(((°>
09-16-2011, 08:23 PM #6
In general, the coil is supported by (attached to) the furnace. Some installations even have a flexible coupling between the coil and the supply ductwork, which wouldn't support any weight. The ductwork should not be supporting the weight of the coil.
09-16-2011, 09:29 PM #7Professional Member*
- Join Date
- Mar 2011
- Galveston Texas
If your new heater is shorter then the old one the installers will usually make some sort of transition to make up the difference, now if it's a real small difference and you have flex ducts instead of hard pipe for duct work and there is enough extra they may just lower it down to sit atop the new heater. without seeing our setup i can't tell you for sure, but your installers should be able to handle it with very little problems.
09-17-2011, 08:37 AM #8Professional Member*
- Join Date
- Jul 2006
have the installers inspect and clean the coil while the furnace is removed
09-17-2011, 11:23 PM #9
[QUOTE=sktn77a;11297272]In general, the coil is supported by (attached to) the furnace. Some installations even have a flexible coupling between the coil and the supply ductwork, which wouldn't support any weight. The ductwork should not be supporting the weight of the coil.[/QUOTE]
Thats not entirely true.
There's plenty of times where you can build a support system in the plenum, and have to."Better tell the sandman to stay away, because we're gonna be workin on this one all night."
"Dude, you need more than 2 wires to a condenser to run a 2 stage heatpump."
"Just get it done son."
09-18-2011, 12:58 PM #10
Inspection and cleaning of the existing coil is recommended when you change out the furnace, some even install inspection ports just for future inspections, if the coil is sitting directly on the furnace not much chance for that, eh? We have never seen a plug coil right?
RTFM is also the rule of thumb for any installation.