You start with the factory charge and line length estimate adjustment.
Originally Posted by HVACTechNC
Then, you MEASURE. You adjust the charge based on that data, using the correct method, based on the metering device being used.
[Avatar photo from a Florida training accident. Everyone walked away.]
2 Tim 3:16-17
RSES CMS, HVAC Electrical Specialist
AOP Forum Rules:
It's not rocket-science...
It's electromechanical thermodynamic engineering
I agree with the charging by WB temp. Which can be measured by a physcrometer .If you get a field piece hs35 or 36 ,it has a cool little head attachment that fits right in the case ,get that and a superheat chart and you will get +/- 3 degrees everytime gauranteed or yo money back
"I just think things should work properly"
Freon is a brand name-word