Results 1 to 3 of 3
09-03-2011, 10:14 AM #1
Was working on a walk-in cooler for a new customer, box temp would get below, 45 degrees, after looking over the unit, and trying to adjust the superheat on the tx-valve was getting some really strange reading. Pulled the insulation off of the pipe and the bulb come right out of the clamps. Not to mentions the bulb was acroos two pipe joints.
09-03-2011, 12:36 PM #2Professional Member*
- Join Date
- Dec 2002
- SouthEast NC ICW & Piedmont Foothills
at least it wasn't still coiled upIt`s better to be silent and thought the fool; than speak and remove all doubt.
09-03-2011, 12:37 PM #3
True, but a little common sense goes a long way, Or some training might go a little futher.