Does anyone know the minimum opening size for combustion/ventilation air for a natural draft furnace
located in an unfinished basement or crawlspace in TN?
Is more than one opening required? I have always used a minimum of 1 sq. ft for any furnace and 1 sq. inch per 1000 BTUs of the furnace input. Thanks.