So I am working on a mcquay water-sourced heat pump and heres what i found. Low press 60, high press 235, superheat 45, sc 26. DAT 53, RAT 83. Amps 4.5 (slowly rise until compressor goes off on o/l) If the compressor didn't go off on overload I would just assume that I had a restricted metering device or evaporator. The fact that its going off on O/L is making me think otherwise because In a mild m/d or evap restriction, amp draw is usually low right? Any help would be great!