Got a package h.p.,condenser fan wont run...208/230.
got 110v at y @capasator 110v at brown capasator and 110v feeding back though black?
Are you in the HVAC field?
(we can't help DIY, due to site rules )
Must be new to the trade then, very new.
Fill out your profile.
Contractor locator map
How many times must one fix something before it is fixed?
do you have 220 though? does the compressor run?
Before this becomes a troubleshooting lesson in the wrong section, I'm closing this thread. To the OP, get approved for PRO status if you are in the HVAC, and post your question in the PRO section.