somebody please fill me in on Goodman being derated so far when converted to LP??? example a 115,000 puts out 93,000 btu and a 70,000 btu puts out 55,000 btu..... why so low? I'm guessin to help out the longevity of the heat exchanger?
Results 1 to 4 of 4
Thread: goodman derating.. why?
Used Equipment - Buy, Sell, Save!