Coil Keeps Freezing Up, We Don't Know Why
Previous company she had out gave her the ole gas-n-go. Unit still icing over. I pulled the filter out and it looked new (always a warning sign). I opened up the plenum and found:
Of course, I couldn't just clean the evap and leave the blower unattended. I pulled the blower and discovered this gem:
"Oh, we ran it without a filter for a few weeks until we could get a new one."
Good? Bad? I'm the guy with the gun.
Statements made by me are strictly my opinions and do not reflect the opinions of my employer. I am not authorized to make any official statements on behalf of my employer.
Any technical advice offered by me is for educational purposes only, all HVAC related repairs should only be attempted by qualified personnel.
most guys including me, some times just check the filter, but don't open the blower door,this is a good reason to always be a little more inqusitive. nice photo!
Originally Posted by dougfamous
Picture looks like the blower wheel has been cleaned without the motor being cleaned.
Quality work at a fair price with excellent customer service!
Romans Ch's 5-6-7-8
2 Chronicles 7:14
the new filter is usually a warning.
I got scolded by a customer once for pointing out that the old filter, that looked like a piece of cardboard, in the trash can was the issue.
trash can few feet from cond, it was sticking out so I had to look.
unit checked out fine and no call back.
The Food Stamp Program, administered by the U.S. Department of Agriculture, is proud to be distributing the greatest amount of free meals and stamps EVER.
Meanwhile, the National Park Service, administered by the U.S. Department of the Interior, asks us to "Please Do Not Feed the Animals". Their stated reason for this policy "... the animals become dependent on handouts and will not learn to take care of themselves."
from an excerpt by Paul Jacob in Sun City, AZ
Had a no cool call.
The customer was a filter company.
The unit a residential split, the space it served was their filter making area.
The air handler didn't have a filter in it and the evaporator was plugged with scrap filter material.
You would think they would know better.
Waddya mean don't thaw out the frig with a knive?
Just run it backwards for a few weeks, cleans em right up.
Never argue with a crazy man.
Now thats funny.
Originally Posted by knewguy
Karst means cave. So, I search for caves.
You've heard of one of those hog hair filters? That is the new cat hair filter. Lets nothing through, not even air! Only 19.95, and now for a special time, 2 for the price of one. Call now.
Found one today where the evap was on the return side of the furnace and the filter was between the evap and furnace. I guess the coil is supposed to act like a prefilter.
some folks like em hairy...
Few weeks?....how bout a year or two.
You will probably be going back soon to change that blower motor out.
Millions of individuals making their own decisions in the marketplace will always allocate resources better than any centralized government planning process. -- Ronald Reagan
This truly hilarious
Originally Posted by knewguy
America; first we fight for our freedom,
then we make laws to take it away.
-Alfred E Newman
That's a good call, the world need more techs like dougfamous.