Another silly question (sorry):Originally posted by moonman1
The trigger point for the t'stat is probably 1+ degree. If you adjust the setpoint of the t'stat 2 degrees below the indicated room temp, does the unit come on? If so then the discussion of your t'stat should focus on it's sensitivity and ability to bring the sytem on at temp. less than or equal to 1 degree F. Read the IOM carefully to see if a cycling adjustment can be made to improve t'stat performance. Running the furnace blower continuosly can cut the deadband thermal discomfort that you are experiencing.
What's the IOM? Is it the Installation and Operating Manual?? If so, I assume you mean the one for the furnace. Correct?