A limit usually trips due to overheating. The reason why they overheat is because you aren't moving enough air. The system has worked fine for x amount of years and now all the sudden it doesn't work properly. Sounds like something happened to your airflow. Did you move furniture and block vents, are the zone dampers opening fully, if you have a bypass damper is it operating properly. Find out if you have the correct amount of airflow.