NEC Table 300.5
Assuming the circuit discussed;
RMC 6" minimum.
RNC (rigid plastic) 18" minimum.
If it was under cncrete the depth decreases.
If it was under a road, driveway, or airport runway the depth increases, etc. etc.
Results 14 to 15 of 15
Thread: National electrical code