OUTSIDE Condensor model JS3BA-030KA
iHAVE PRESTON GUIDE but only to 2001 this is newer, i think not shore on the year.
wanted to know if its under warranty cause customers old one burnt out o ohm to run and start windings
went out breaker was kicking checked unit dual capacitor 35/5 mounted on unit with metal bracket capacitor terminal wire to compressor touching side of metal burnt out compressor.
also this homeowner is a second owner after install they told me.
FOUND IT one year old if that and its under warranty
also found dealer great
i need to get a list of all the manufacturers phone numbers