20% DowFrost (PG) freezes at 19.2F.
20% DowTherm (EG) freezes at 17.9F
if you slow your glycol flow down below the recommended minimum flow rate, the glycol next to the tubes can freeze and the glycol in the middle of the tube will not freeze. so then your chiller tries harder and gets less cooling out of it.
i don't know about glycol breaking down, but pudding......
Don't step on my favorite part of the Constitution just to point out your favorite part.
Political Correctness is forced on you because you have forgotten decency.