You really got to watch it with those condensers...it's like the Carrier coil-in-a-coil design. You got to take the top off the unit and really clean in between them, otherwise it's just cosmetic...at least they put the compressor toward the opening for you--or did someone build the structure around the CU?
Leadership...the ability to move forward even when you've burned your foot.
That is the dryer vent that fell apart, and Yes those short inner coils suck to split and clean. It doesnt do any good to have 5 inches of clearence on the coil sides either, and who cares about the comressor I will NEVER change it. I would sooner put in a side discharge unit. Also did you notice that box fan? It is wired into the contactor actually the duplex outlet is wired into the contactor the fan is just plugged into it. What a set-up!! And by the way who the hell cleans condensers WITHOUT taking the top off??
A proffessional is someone who does his best work even when he doesnt want to.