OK here we go. the guy was out again here yesterday he said i got a "twenty" degree split and he said thats all he needs to give me thats the law in florida. house still won't cool below 78 F during the day. His little infrared meter reads that out of most of the vents the air comes out 56 F and only in the other side of the house where bedroom is and masterbath he gets a 69 F reading.
he says all is normal. he insists its not the t ton airhandler thats the problem nor is it mismatched with the 4 ton outside unit. he said the head preassure outside is 265 and thats normal too.
he had exchanged the piston to match.
What i still DONT understand why were we able LAST summer and the summer before to cool the house down to 70-73 F during hot days and now he just tells me its normal u can't cool below 78 F.
Any suggestions? Is he right with all he says? He said there is NOTHING else he can do for me.
Should i now finally get someone out with a 2nd opinion?
When i told him that if I do find out its totally mismatched our his fault that i want him then to take the unit out and refund me the money he smiles and says oh sorry florida has a "buyer be aware" law and he didn't have to do that. So he told me not to even go that way!