I am about to replace the furnace and the AC unite. The furnace is going to be 75,000 92% with seal combustion.
The installer wants to install a 10 SEER condensing unite with model # HAC030AKC4 and a coil model # EDP30F19C2. Is this a good combiantion on a 2 1/2 tons unite. I am located
in the chicagoland are. Thanks for your comments!!!
Looks kosher to me.
Both the coil and condenser models numbers indicate 30K btu.No problem.
So, the furnace is a H9MPD075F12B (single stage)?
I'd personally opt for a furnace upgrade to a 2-stage unit.
The 10 seer is ok (the HAC is a good model), but the TXV coil EXD30F19C would be better for humidity control and efficiency.
Have you had a 'load calc' done on your home?
thanks for the comments,
I would asked about upgrading to the TVX coil. He was the only installer who perform a J manual calculation and measure the size of the windows and amount of insulation in the attic.
Sounds like you got a winner.
Now just don't be surprised if he is a little higher than the other contractors.
Quality workmanship is PRICELESS!
Just checked yesterday and that is the exact same unit I have, however I have a 3 ton evap. I'm happy with the performance and cost of the system.