I just joined the forum and would like to ask a few
questions about one of A/C systems in a home I just
purchased in April of this year.
The house has two systems. The system for the main part
of the house was not cooling well in the last couple of
weeks when the temperature here in Dallas, TX was ~100 degF.
The best the indoor temp could get during the day was
about 80deg. I have 8-9 inches of blown insulation in the
attic and the house was built in 1986. The main room does
have many windows.
I called an A/C company. They came out and checked the
refirgerant (410A) which seemed a little low. The tech.
said I must have a small leak (most likely in the coil) and
added <1 lb. of 410A while monitoring the pressure and
temperature of the line. I had previously changed the
filter and cleaned the outdoor unit coils. The unit cooled
a bit better after that, but still only reached ~77 deg. in
the middle of the day.
I had the company come back out. This time we looked at
the upstairs unit. It is a Carrier system and here are the
Furance is: Carrier 58CVA090---10116
Upstairs coil is : Carrier CE3AXA042000ABAA
Outside unit is: Carrier 38TXA042300
The second tech. found the following things:
1) The plenum? (metal box on the outlet of the evaporator
coil) was built such that ~35-40% of the coil didn't have
air flow across it. The box inlet is smaller than the
coil outlet. the guys said it was just a poor install.
And that makes sense to me.
2) He said the evaporator coil was only for R-22 and not
rated for 410A pressures. I've read that some coils can
be used for either. The coil says R-22 on it and a max
pressure of 300 PSI. When the first tech added the 410A
the pressure was ~380PSI and when we were done it was
~400PSI. Can anyone tell from the above model numbers
if my coil can be used with 410A?
3) My furance is a Carrier Weathermaker 8000 with variable
speed fan, but the theromstat was a manual mercury
thermostat (with 4-wires) so I am unable to take
advantage of the variable speed capability of the fan.
The second tech recommended that I replace the evaporator
coil with one that is rated for 410A since my current one
probably has a leak in it. Have the plenum rebuilt to allow
better air flow and then install and wire a thermostat that
can utilize the variable speed fan.
I need to get the house cooling better in the Texas heat. I
am looking at adding insulation, but would like to hear
opinions on what steps I should take to get my system
The plenum fix sounds like it needs to be done. I'm not
sure about the need/benefit of changing the evaporator coil.
And I've read how the variable speed fan can help cut
humidity which makes you feel cooler. I'm not sure how that
works or if it would be of benefit in cooling my home.
Thanks for the advice/help in advance.