need some help,split system 2.5 ton the condensing unit
is clean so is the evap coil and the indoor blower.
The outside temp is 93F,suply air 67F return
air 80F hi side psi 220 lo side psi 90 psi,
Where would be the problem since the low side
is at 90psi?
thanks for any help.