I’m waiting to have my second contractor come Tuesday and repair/finish the installation that the first guy dropped the ball on.
I now notice that the furnace, an Amana AMV80905CXA has a 5 ton blower (The original discussion was to install a 4 ton - AMV80704BXA - blower). The Outside AC unit is an Amana RCE42C2A 3.5 ton.
So I am at a crossroads - should I have the new contractor simply supply the missing transition - or should I replace the 5 ton blower with a 4 ton?
Will just keeping the 5 ton pose any significant problem down the road?
Man, this is a nightmare...