Have a processer going nuts. It's got the front pannel controls with the rocker switches simaler to series R machines . It's air cooled with chiller in basement with 4 scroll comps. Any way I it will run and **** down when it feels like. It will have a code 70 [start inhibit] run for two min then have a code 11 ]pump down and shut off. I did catch it flash code 100 [remote shut down] then back to 70 back and forth within seconds, this is with the remote start/stop terms jumped out. I tried calling the series R plant I think it's in wisconsin but the # changed. I hate to just start throwing new boards in the unit with out more info. Any sugestions?