The unit is off by on the t-stat and the condenser fan is spinning in the reverse direction. When stat calls for cooling it stops and goes the correct direction. Then when you cycle unit to off position the fan slows down and goes the reverse direction again. It is getting 120V feedback from somewhere. I didnt have alot of time to troubleshoot this. Was the first time i saw this. I figure there is a feedback coming from one of the legs.
Or there is
a: defective disconnect
b: bad contactor
c: feedback coming from panel somewhere
D: defective fan motor
Just curious if anyone has seen this issue before? I didnt have alot of time to stay there.. thanks for the feedback