Liebert modbus intergation into ALC's Eikon program
Thanks for the offer of help.
Yes, the Liebert unit does have the proper modbus interface card.
Here's an "example" of what I'm looking for:
modbus://uint/40078/1 which could equal compressor 1 lockout
modbus://uint/AI:40090/1 which could equal the cooling setpoint
There may also be an multiplier which needs to be added and/or divided by too get correct result (reading).
I used to have the Automated Logic "Eikon" files that had all the correct Liebert unit modbus integration connections but lost it. Now I'm unsure about several connection statements. If someone has the entire "Eikon" Liebert file that would be great but will settle for the written out list of connections as well.
FYI, that could get you into trouble. With the newer versions of logicbuilder you just open the equipment file directly. IF you upgrade an old equipment file wiith logicbuilder and save the equipment file directly there is still a eiw or similar file included under what i think is a legacy folder in the equipment zip but it is NOT up to date, that is just the original file for reference and it doesn't contain the latest changes. Basically once you go new style logicbuiler you should to stay with it. No reason not to either as far as i know, you can use the new equipment files as far back as 2.0 at least.
Harris Integrated Solutions
Formerly Liebert (Emerson Network Power)
Expressed opinions are my own