Question about a stepdown transformer
I am looking to find the rated amps for the sencondary of a stepdown transformer. Three phase primary is 460/575V, secondary 230V, 200VA. I am not sure if I should calculate the secondary side of the transformer as 3 phase or single since it is only 2 wires coming out of the secondary.
3 phase- 200/230/1.73= .5 Amps
Single Phase- 200/230= .87 Amps
I am not sure which is correct and I could really use the help thanks.
There are no three phase transformers, just multple transformers placed together in a package.
In this case you have 1 transformer fed from 3 phase. However it is only tied to 2 of the 3 phases.
2 wires in 2 wires out, figure it as single phase.
IF this was a three phase transformer your calculation is incorect.
You have to allow for the 3 phases of power.
The equation is I = (KVA x 1000)/ (1.73 x E)
Assume this is a 20KVA 3 phase transformer instead of 200VA single phase.
(20 x 1000) / (1.73 x 230)
20000 / 397.9 = 50.26 amps
Last edited by wolfdog; 02-10-2011 at 07:36 PM.
If it only has two wires coming out of the secondary it is single phase. I am not sure I understand you by saying, "There are no three phase transformers" when in fact there are? They are in delta or wye configurations
The "Only" thing Wolfdog has been in error about is his chosing a puny 9mm against a full house 45ACP. His statement that there is no such thing as a 3ph. transformer is correct. Just because a 3ph transformer looks good on a schematic diagram, in all actuality it is nothing more than single phase transformers connected in Delta-Delta, Wye-Delta or Delta-Wye configuration.
Now....If I could only get da' Wolfdog seeing straight on the 9mm/45 issue all would be well.
Ain't "None" of us as smart as "All" of us..
I'd rather have a 9mm over a 45 as well, for many reasons. That is why I carry a 9mm and not a 45acp
I'm open to negotiation RichardL.
don't forget wye-wye...but who would use those? stupid triplens!
Originally Posted by RichardL
as for the transformer...i do not believe that he has a 3 phase transformer PRIMARY and a single phase SECONDARY. my guess is that his transformer is a multi-tap PRIMARY transformer.
approximately 0.87 amps would be correct for 230 VAC, single phase.
"Mother" is the name for God on the lips and hearts of children....The Crow
I don't believe I have ever met a Wye/Wye transformer configuration.
Delta/Delta for isolation and/or step down.
Delta/wye to produce a neutral and/or step down.
Wye/delta to step up.
The obvious question is Wye?
Richardl both choices less than optimal
40 cal better ballistics and knockdown!
If I could only get da' Wolfdog seeing straight on the 9mm/45 issue all would be well.
You have got to learn from other people's mistakes! Because God knows you don't live long enough to make them all yourself !!!!!!!!