I responded to a call where the evaporator and the condenser the evap is 3 tons and the condenser is 5 ton how can I correct this problem with out changing what's there and costing the owner crazy money.
I have three years in the trade one in school. Mostly walk ins and reach in units in time
The three ton unit. Have a txv for three ton. As well would a bigger txv hurt or just flood the evaporator. Or could I add a nother evap on to take away some refrigerant from the other but keep the regular condenser.