I've just installed 3 Goodman heat pumps, ranging from 1.5 tons to 2.5 tons. I've gotten 2 call backs today (Sunday) and the condensing units are not shutting off when the t-stat is statisfied. They won't even shut off when I turn the t-stat to the "OFF" position. I had to pull the disconnect to get them to shut off.
My question is has anyone heard if there were a bad batch of condenser boards that got out into the real world? Or am I totally missing something?