I got a 23XL Carrier screw chiller that just had it’s Benshaw soft starter replaced (complete RSM6B unit). The chiller was down approximately 5 weeks. Upon attempting startup, the chiller faults on “High Condenser Pressure”. The condenser pressure read about 80 psi, which coincides with the oil pressure reading. The discharge transducer is good. The threshold value is set at 230 psi. The discharge pressure switch and the CW and CDW differential pressure switches were closed. There were no faults displayed on the starter. Benshaw shall be contacted on Monday. Does anyone know what the problem may be? Thanks.