Results 14 to 16 of 16
03-20-2005, 11:10 PM #14
If your boiler is running longer as it gets colder out, a larger circ is not going to help.
Thats what the boiler should do.
You should look at your weather stripping, and think about adding insulation to your walls, to cut down on the amount of heat you need.
Contractor locator map
How many times must one fix something before it is fixed?
03-20-2005, 11:35 PM #15
Is there an expansion tank and is it before or after the circ pump? If so was it's position changed when the replacements were made?Quote
Engineers like to solve problems. If there are no problems handily available, they will create their own." Scott Adams
"We can't solve problems by using the same kind of thinking we used when we created them."
03-20-2005, 11:50 PM #16Regular Guest
- Join Date
- Jan 2005
The 110pump does have a little more gpm than 007, on the other hand the 007 has a little more head room I think its a wash. Considering the boiler was down sized 20000 btu outdoor reset may be just what you need with a P/S near boiler piping, depending on type of boiler. Find a profess to help you make the right choices.