Results 14 to 15 of 15
Thread: Transite flue and condensation
03-07-2005, 12:55 PM #14Regular Guest
- Join Date
- Jul 2004
You might be able to adjust the temperature rise on the furnace and thereby increase the flue temperature and prevent condensation. That's just a blower adjustment but must be kept within an acceptable range.
03-07-2005, 02:04 PM #15
i would try to get a flex liner down thru chimney. would not be in a big rush to deal with ripping out asbestos pipe. any 80% furnace would have chance of same problem.
if he had noticed it coud be a problem you would have paid for it anyway. bite the bullet and just get it fixed before moisture destroys pipe.