guys i need some help on this one.i was called out on water
running into bin call its a hosizaki km800mwe water cooled
r-22 cuber. found water regulating valve leaking machine had ice in it almost full even saw it drop replaced regulating valve w/ same new unit recovered gas all 1 lb 12oz
evac to 300 mics recharged w/ dial a charge now no ice making after 5 mins of freeze have 22# low 280# hi after 7 min 16# low 280# hi after 10 min 22#low 350# hi gets a little formation of cubes on right evap nothing on left evap
checked dump valve not leaking checked water valve not leaking water pouring out of cond cold cond cold the drier outlet side 1/4 of it has frost and the line coming out of the drier has frost drier is original i know i should of changed it but why the hi head pressure water is going through cond and pouring out but still hi head and no production also recharged w/ new r-22 could it be the drier would appreciate any help thanks in advance the serial # is c20187k its an older unit.